Characteristic dimensions table
ŠUKOPLAM MEGA 1000 - 2500 kW
Boilers type Šukoplam MEGA with power range 1000-2500 kW are ment primarily for combustion of bulk solid fuel (wood,coal) as well as diverse wood waste.Boiler is ment to work coupled with exhaust fumes fan so that quality of combustion and boiler efficiency can be as high as it can.Coupled with special „adiabatic“ firebox (gas generator) wood chips, pellet, fruit stones and small chipped wood waste with moisture content up to 60% can be combusted. This combustion is done totally automated, while combustion of chunk solid fuel is done in the boiler firebox by manually loading through spacious side boiler door.Because of the great depth of the boiler firebox, boiler has two side doors for ashtray cleaning and easy access to the boiler firebox grate.
Boiler is constructed as „three drafted“ with two rows of flue pipes which means that products of combustion pass water area in three occasions maximasing the heat exchange.First heat exchange is in boiler firebox, mostly by methods of irradiation, through large surface area of boiler firebox, second heat exchange is in first row of flue pipes mostly by methods of irradiation and convection, and the third heat exchange is in the second row of flue pipes before the flue gasses exit the boiler mostly by methods of coduction and convection.Boiler body is well insulated with mineral wool and boiler sheeting is protected with painting or powder coating processes.
Boiler is ment for production of hot water in operating mode 110/90ºC and 90/70ºC with maximum allowed work pressure of 3bar.At buyer deman boiler can be equiped with automatic ash removal as well as automatic cleaning of flue pipes.
Regulation of air flow needed for combustion of chunk solid fuel is done with draft regulator which moves the flap on the bottom boiler door and by doing so increases or decreases the amount of air needed for the combustion. When using gas generator coupled with the boiler regulation of air flow needed for the combustion is done through the generator and boiler automatic controler.
Protection of boiler from increased pressure is done by installing the safety valve on the appropriate place on the boiler, while protection of the boiler from increased temperatures is done by installing the safety heat exchanger which,if the need arises, cools down the boiler.